|Published (Last):||15 November 2016|
|PDF File Size:||19.92 Mb|
|ePub File Size:||8.1 Mb|
|Price:||Free* [*Free Regsitration Required]|
GB0 G Technical changes reserved! The terminal assignment and.. Any deviation from those rules is only admissible if the same degree of safety can be ensured with different means. Installations within the European Community are primarily subject to all EU regulations defining the current standards for security systems.
The language is defined with the 2-digits of the part number, e. FB Micro module Power supply module Part No. Application: With this configuration, for example, a single control panel with an analog loop and max.
Due to the depth of the printer, the Basic module and all of the plug-in cards are integrated into a separate housing beneath. The emergency power supply with max. This internal primary loop number is composed of the control panel number, the slot and the assembly number. This fastening is intended for a different housing use. Danger - Electrical shock! Disconnect all power from the panel before carrying out any installation work.
The panel may only be operated while the cabinet is closed. To ease the further assembling and mounting please observe the given mounting sequence. If required for dismantling, loosen the 4 fixing screws and remove the front part of the housing.
Remove the appropriate 2 plastic plates from panels and extension housing 2. Push the plastic connector bracket in each originated gap.
Avoid mechanical stressing. It may only be commissioned after correct mounting on a wall or other mounting surface of sufficient strength to support the weight of the unit. Fasten it using appropriate devices, e. Only remove or insert modules when the FACP is voltage free.
Page Protective And Functional Earth The base module is connected to the rear panel of the cabinet by means of metal spacers and screws. Observe the information and technical specifications of the battery manufacturer and the VdS-guidelines for deep charged batteries. Page 32 Fix the mechanical battery fastener by inserting the two screws Fig. Pay attention to the settings on the power.. The software tools from Version V1. A single contact per housing is integrated by factory settings. The required interface to connect external devices is selected by the Service software tools from Version V1.
Assignment of the eight screw terminals will depend on the micro module type used. May also be used as a freely programmable relay. Relay K1 Selection of operating mode and emergency function by means of jumpers. The actual connection of the eight terminals depends on the type of module used. Connections are available for each micro module. The pin assignment of the eight screw terminals depends on the employed type of micro module.
In this case the integration of an Field device module is impossible. Extension module with a single micro module slot Part No. Only remove or insert micro modules when the FACP is voltage free. The analog loop is configured with Programming software tools from index V1. Part No. Page Technical Data Analog Loop Module The permitted loop length depends on the number and type of the loop devices and may differ from the max.
D0 per IQ8Control C as well as max. Use an appropriate screwdriver for setting switches S1 x1 and S2 x Mixed operation of fibre optical and conventional wiring within a common network is possible. You may connect up to three external devices to this micro module. In the event of an incident, polarity changes between monitoring and activation voltage at the relay connection terminals.
This application involves feeding an external voltage e. Relay assignment is programmed with the service PC and programming software tools from version V1. Assignment of the serial interface type is programmed with the service PC and software tools from version V1.
With the Fire Alarm Control Panel, a connection for a master box module is integrated in the Field device module. Selecting the activation time for the MFAB activation for approx. Contact rating: max. The service level is protected from unauthorised access by a numeric authorisation code.
Additionally, it is possible to replace single detectors in operative analog loops e. Page St : the converse. In all non-addressable detectors Series , the detector zone state is simulated. The simulation of control states in an essernet network is impossible.
In addition, the contents of the internal event memory of the control panel can be printed out on a local protocol printer. The last events, such as alarms, malfunctions, switch-offs and operating authorisations are stored in the event memory in chronological order.
Page Diagnostic Display The diagnostic display enables, e. Switching on the display on the fire alarm control panel The following tables show the individual micro modules, each with the valid range of analogue values. The meanings of these codes and measures for correcting the error condition are given in the following table.
Check the installed detector if the surrounding area is humid. Use protective Clean detector and check it with measures if necessary, e. Detector unable to correctly Check detector base wiring. Fault occurs while loop is being switched on: switch off loop and switch back on again after minutes. If this change is not desired, There are more detectors on the connect service PC and run loop than programmed in the a configuration check.
Re- customer data. Check if the detector type The IQ8Quad detector circuit has change is desired; if yes, Otherwise, install desired been changed at the detector reprogram the customer data detector and restart location. A detector could not be reset Replace detector. The esserbus door control transponder is operated as a bus device on the analog loop of the IQ8Control fire alarm system. Unassigned RF devices consume approx. This mounting kit comprises of a mounting base and a standard 35 mm top hat rail C-mounting.
In order to facilitate mounting and removal, the top hat rail is fitted to the mounting base by means of two screws. Ensure that no cables are pinched or damaged when installi ng or removing the assembly. Language identification, e.
Ribbon cable Fig. Panel front for heat transfer printer with paper take-up reel Part No.
ESSER IQ8 PDF
Wir haben Installation Instruction. Da wird es mal Zeit, dass Still need help after reading the user manual? Find solutions to your esser iq8 question. No matter whether multilingual speech alarm, flexible signal combination or user-friendly programming.. Send to a friend.
Esser iq8 installationsanleitung